What is the correct DCM-PRO cable spacing?
Correct DCM-PRO Cable Spacing
When loose-laying the DCM-PRO cable on the floor, maintain a consistent cable spacing of no less than 3” and no more than 4”.
First, uniform consistent spacing is essential for even heating throughout your space. Ensure that the minimum bending radius is no less than 1” for the heating cable.
Below is the formula for calculate your DCM-PRO spacing. This formula is based on the heated square footage of your room and the heating system you are installing. To start, insert values to complete calculation.
OCS (On Center Spacing) = (Area (sqft) * 12) / Length (ft)
For more information, please refer to the installation manual.