We recommend using a conduit 1/2 conduit for one lead or a 3/4″ conduit if connecting two systems to one thermostat. In addition, we recommend a separate 1/2″ conduit for the floor sensor.
In order to properly mount your 4iE thermostat, you will need a back-box as well as a mud-ring. Warmup can recommend compatible items.
This page explains why Warmup does not recommend you cut the wire for any reason and provides solutions to having too much cable.
We have provided helpful reminders to ensure a successful installation. Click “Read More” for details.
Follow these simple mounting instructions. Click “Read More” for details.
Easy to install, take the time to review the installation procedure for the best results. Always use a licensed electician. Click “Read More” for instructions.
The Warmup DCM-PRO or StickyMat system may be used under carpet tiles as long as it is embedded in latex based modified polymer self-leveling compound prior to the installation of the carpet tiles.
So either the installer puts a DIN rail on the wall or cabinet, or they can utilize the four mounting holes in the corners of the housing and screw it to a surface.
The thermostat should be installed inside a square 4”x4” back box with a single mud ring mounted horizontally (also called plaster ring).
The proper distance to space the mats should be 5 feet on center or 3ft between mats. Please refer to the installation manual for more details regarding your snowmelt installation.